Pullborough STW Inlet Screen Upgrade
A Wastewater Case Study Huber Technology completed the inlet screen upgrade at Pulborough STW installing 2 Ro9/700's on an elevatated inlet works.
Working with BTU, Southern Waters small projects delivery team, we looked at various different options to replace the old worn out 25mm Parkwood bar screen and Parkwood dewaterer. The P.E for Pulborough was 8,352. The consented FFT is 62l/s. Flows from the terminal pump station recorded flows of up to 160l/s. the existing screens were allowing unscreened influent into the balance to the storm tanks and blocking downstream pumps.
Huber Technology Supplied
• 2 Ro9/700/6 Combined Screens
• Control panels
• M&E Installation
Objective & Solution
The maximum size Ro9/700 was agreed and fitted to meet the maximum inflow of 160l/s. Also it was decided to fit 2 screens and remove the existing bypass bar screen.
Quotes- Working with BTU to delivery this project within budget and on time was a challenge for everyone. But, with good communication between BTU, Southern Water and Huber, the end result was a great success.
Adrian Heneghan – Huber Area Manager
More than happy with the screens. Now I have time to work on other parts of the site and not have to worry about lifting and clearing pumps.
Ricky Corkett – Southern Water Site Operator
For more information please contact Adrian Heneghan 07540 667094, email email@example.com or visit our website www.huber.co.uk