Designer liner proves perfect solution for pump station
The Danish infrastructure firm Per Aarsleff's new pipe division has carried out a cost-effective - and environmentally friendly - lining project in Suffolk. UK managing director, Terry Bolsher, explains the process
Per Aarsleff’s recently formed pipe technologies division has successfully completed its first pipeline repair on a damaged pumping station discharge pipeline at Bawdsey, on the East Suffolk coast.
The deformed and leaking cast iron pipeline was quickly restored with an Aarsleff cured-in-place resin impregnated polyester thin walled one piece liner, forming a joint free, leak proof smooth bore pipe within a pipe.
Bawdsey land drainage pumping station and its 450mm diameter discharge pipeline were built in the late 1950s to serve an agricultural catchment of nearly 13km2, half of which lies at (or below) mean sea level.
The station automatically controls water levels and discharges surface water drainage through the pipeline, under a flood defence embankment and into the tidal estuary of the River Deben.
The overall pipe is about 30m long, but the 22m long section, from the pumping station to the outfall, has deformed under the weight of the embankment and sunk about 250mm into a shallow ‘U’ shape.
When the pump operates at its flow of 0.45m3/s and pressure head of 5m, water is forced out of the damaged pipe’s open joints, jeopardizing the integrity of the flood defences.
A swallow hole appeared in the embankment, forcing the Environment Agency, which is responsible for the embankment, and the East Suffolk Internal Drainage Board (ESIDB), responsible for Bawdsey Pumping Station, to act quickly.
The ESIDB is one of a consortium of five boards making up the Water Management Alliance (WMA), which together protect about 1,220km2 of East Anglia.
There was an acute risk of an embankment breach and the WMA looked at alternative repair options.
“We had to act quickly and considered various alternatives, including replacing the entire section of pipe, but that would have required major invasive surgery to the embankment,” says WMA district engineer Ian Hart.
“Instead we opted for a less invasive option of relining the pipe without the need for any excavation, in the spirit of modern, keyhole surgery.
“I contacted Aarsleff and they confirmed the feasibility of repairing the pipeline insitu with a tailor made liner. We then appointed the local civil engineering contractor Breheny to oversee the repair as they had rebuilt the pumping station in 2003/4. Aarsleff purpose made the liner to suit and installed it in a slick and professional operation.”
Breheny provided clear unobstructed access to the pump house, removed the pipeline inspection cover within the pumping station and opened the outfall flap valve to allow Aarsleff to make a start on the lining during low tide.
A thin plastic pre-liner, with a blanked end, was first inserted into the damaged pipeline using compressed air to protect the main resin-impregnated polyester liner during installation.
The main liner was designed and made by Aarsleff’s in-house designers to withstand the positive and negative pressures and the high flow rates generated when the pump operates.
It was made inside out from resin impregnated thin layers of special needle felt so that the outside surface eventually became the inner smooth bore surface when the liner was inverted into the damaged pipeline. The main liner was packed in flake ice during delivery from the factory to site to prevent premature curing.
At the pump house the liner was wound into the special inversion drum, which was positioned close to the pump house entrance.
A length of liner, twice the distance from the drum to the pipeline manhole, was pulled out of the drum.
This protruding section was then turned back on itself so the inside of the liner was now on the outside.
It was pushed onto the outlet nozzle of the inversion drum and held in place with special clamping bands. The liner was then lowered down into the manhole and guided by hand a short distance into the pre-liner and into the entrance of the damaged 22m long pipeline.
The inversion drum was then pressurised with compressed air, which forced the liner, with its closed end, to rapidly unwind from the drum and unfold and invert itself through and out of the open end of the damaged pipeline.
The inversion process only took a few seconds with the air pressure forcing the liner through the prelined damaged pipe and against the wall, which effectively acted as a former for the new lining.
A steam pressure hose was then connected from a special boiler to the inversion drum to heat up the liner. At the same time a steam exhaust pipe was also inserted into the exposed section of liner protruding from the outfall.
Temperature probes were attached to the liner, which was gradually heated by the steam to 110°C and held for four hours to cure the resin-impregnated, 13mm thick liner. By using steam curing, the required high temperature could be maintained, even though the end of the liner was submerged during high tide.
The entire liner inversion and curing process was controlled and monitored by a computer on board a self-contained lorry fitted with highly advanced, purpose built installation equipment, including the boiler and compressors, needed to perform the no-dig, cured- in-place pipe (CIPP) process.
After curing and cooling, the ends of the new liner, which formed a self-supporting pipe within a pipe, were cut off at the next low tide. Aarsleff’s lining crew completed their work in just one and half days and Breheny followed on, restoring the outfall flap valve and returning the pump house to full working order.
The repair to the Bawdsey pipeline was completed without any excavation or disturbance of the pipeline and was done in a fraction of the time and at a fraction of the cost it would have taken using conventional, open-cut pipe replacement methods.
Initial Aarsleff CIPP lining contracts in the UK will be carried out by experienced teams from its parent company Per Aarsleff A/S in Denmark, using their own computer controlled installation equipment and Aarsleff manufactured CIPP liners, but managed and supported from the UK’s Newark headquarters.
The company’s Danish parent has considerable resources and pipeline renewal expertise with its long established CIPP restoration technique for the renewal of horizontal and vertical pipelines in the ground or in buildings.
The Aarsleff CIPP process is a highly cost effective and environmentally friendly no-dig solution for the repair and renewal of sewers and other damaged and leaking pipes, as it does not require any excavation.
The Aarsleff CIPP lining system can be used to renovate pipes from 60mm up to 3m diameter. The self-supporting bespoke linings are available in various thicknesses to cater for different loadings, and lateral connections up to 18m long are also possible.
© Faversham House Ltd 2023 edie news articles may be copied or forwarded for individual use only. No other reproduction or distribution is permitted without prior written consent.