The perfect predictive maintenance solution
Wessex Water, serving an area of the South-West that covers 10,000sq km and supplying 1.25 million people with around 353 million litres of water a day, is investing in new maintenance technology to ensure the company's plants continue to run at optimised levels with equipment that is running effectively. As part of Wessex Water's investment, the Artesis MCM (Motor Condition Monitor) was piloted over a period of 18 months to demonstrate its capabilities, particularly in the prediction of borehole pump failures.
The easy-to-use MCM unit is installed in the motor control cabinet at the plant and only requires connection to the motor supply cables to continuously monitor the whole pump assembly, resulting in a low start-up cost and no requirement to access the driven equipment for any sensor installation. On completion of training, the Artesis MCM system provides a report highlighting any pre-existing faults in the machinery. It then monitors for any deterioration and automatically recognises and alerts the user to electrical and mechanical faults. Using GPRS technology, the team at Artesis remotely connect to the MCM unit installed onsite and monitor the equipment to provide up-to-the-minute, accurate asset diagnosis, 24 hours a day.
During the pilot with Wessex Water, Artesis installed MCM units into the motor control cabinets of six pumps including two borehole pumps at a pumping station near Yeovil. The condition monitoring of borehole pumps is especially challenging due to their location underground and the range of different potential failure modes, which many monitoring techniques would struggle to detect. As the MCM solution is installed in the motor starter panel and monitors both the electrical and mechanical parameters of the pump, it is ideal for inaccessible applications such as submersibles and borehole pumps.
Dave Durkin, head of operational services at Wessex Water said, “As a company we actively explore the latest technology in all sectors of our business particularly those that have the potential to improve customer service, reduce our process risks and save money.”
Following the installation in early 2008, Artesis monitored the pumps remotely and provided Wessex Water with detailed diagnoses on the performance of their pumps. Immediately following installation, the initial condition assessment reports identified a number of preexisting problems with the pumps. The
progressive deterioration of these initial faults was then monitored until the point at which corrective action could be taken.
Wessex Water’s main interest in the pilot was in the monitoring of borehole pumps and it was in this area that Artesis proved their ability to accurately diagnose a variety of problems and pinpoint the exact time to carry out maintenance work. Artesis warned Wessex Water on the condition of both borehole pumps in March and their condition was closely monitored. In July, Artesis advised that one of the borehole pumps should be replaced due to an impeller related problem. To evaluate the predictive maintenance solution and demonstrate the accuracy of the MCM system the pump was left and failure
occurred within a couple of days of Artesis’ predicted date. This highly accurate diagnostic performance provided Wessex Water with a failure date within a few days that represents the potential for saving tens of thousands of pounds.
“The accuracy and reliability of this predictive maintenance solution proved remarkable. For a relatively low cost we will be able to install this equipment into our critical assets and save money on maintenance and repairs. The technology will allow us to optimise our maintenance interventions, freeing up resources for other areas,” said Dave Durkin. “We are looking into investing in more MCM units for installation in our plants across the Wessex Water area.”
“We are delighted with the performance of our MCM solution in this joint evaluation with Wessex Water,” said Geoff Walker, director at
Artesis. “We had confidence that predictive maintenance would provide the industry with the perfect strategy for the upkeep of critical assets and this demonstrates MCM’s unrivalled ability to accurately and reliably diagnose problems and provide detailed maintenance information.”
© Faversham House Ltd 2023 edie news articles may be copied or forwarded for individual use only. No other reproduction or distribution is permitted without prior written consent.
Please login or Register to leave a comment.